A3221407 - LÜTZE SILFLEX® Tray-ER PVC with UL/TC-ER/WTTC/MTW/CE Approvals
with UL/TC-ER/WTTC/MTW/CE Approvals
- Multi-conductor cable for tray applications, with exposed run (open wiring) approval
- Compliant with NFPA 79 for machine tool wiring
- TC-ER for use with cable trays without conduit, which can reduce material and labor costs
- Machine tools, machine and plant construction, HVAC technology, assembly and production lines, and other industrial applications
- WTTC – wind turbine tray cable rating for use in wind power generation
- Dry, damp and wet conditions
- Flexible design with Nylon for crush impact resistance per UL 1277 and easy installation
- Specially formulated jacket for oil resistance
- Non-wicking fillers
- Sunlight resistant
- Direct burial
- UL Type TC-Exposed Run
- Talc free
- Silicone free
- AWG conductor
- CU-wire bare
- with white number print
- Oil resistant
- UV resistant (normal lighting conditions)
- 600 V TC-ER
- 1000 V WTTC
- UL Type MTW or DP-1
- Meets NEC 336,392
- Class I & II, Div. 2
- Class 1 Div. 2 per NEC
- 501, 502, 505
- cUL TC
- CIC FT4
- UL 1277
A3221407 LÜTZE SILFLEX Tray-ER PVC Data sheetDownload, PDF 321 KB
Frequently asked Questions
Which UL approvals are available for cables?
In America, the UL (Underwriters Laboratories) testing institute is a major institution for testing and approving electrical systems. The relevant approvals can apply to entire systems as well as individual components.
UL categorises cables into the UL recognized approval in compliance with the 758 standard "Appliance Wiring Material" (AWM) and various listings. AWM (Appliance Wiring Material) is based on a modular system where cables with an AWM approval can be made up of separate insulation and outer jacket approvals issued by the manufacturer. UL Listed involves subjecting the entire cable to UL testing.
The 2007 edition of the American NFPA 79 Electrical Standard for Industrial Machinery prohibited the use of AWM wires and cables in machinery cabling and explicitly demanded a UL Listing. This proved in many cases unpractical as for many applications there is no legislation to which a listing could be applied. For this reason, this regulation was modified in NFPA 79, edition 2012 and the use of AWMs is now permitted under certain conditions.
How much electricity can a cable transfer?
The amperage range of a cable depends on the cable cross-section and the heat resistance of the insulation material as higher currents heat up the cable to higher temperatures. Selecting the correct cable is the responsibility of the system planner as the cable manufacturer is not familiar with the specific application. Details can be found in the national standards and legislations such as VDE 0298-4 or VDE 0100.
Why is the temperature range divided into static and moving?
Flexible control cables are mainly insulated and covered with thermoplastic. When subject to high temperatures, thermoplastics become soft and malleable. This explains the various limit temperatures: with fixed installation cables it is not a problem when the plastics become soft. However, when the cables are moved, the plastic can be deformed and the cables can become damaged.
This also applies when the plastic becomes brittle at low temperatures.
What is the copper index?
As copper is a listed precious metal, the copper content in a cable is calculated depending on the current listed price. This calculation is based on the amount of copper that is present in the rated cross sections of the copper cables and shielding.
What does the cable category stand for?
The copper conductors in flexible cables usually comprise of numerous thin wires that are twisted together. In comparison to a single copper wire, in which the cross section corresponds to the sum of the single wires, twisted copper wires deliver a considerably higher ductility of the conductor and the entire cable. The international IEC 60228 standard specifies the wire thickness and electrical resistance for copper strands in various categories. The higher the category, the finer the wires:
Category 1: Massive conductors
Category 2: Multi-stranded conductors
Category 5: Finely stranded conductors
Category 6: Superfine stranded conductors
What is the difference between bending and torsion?
Different types of movement require different cable constructions. A cable with optimised bending load has different construction parameters than one designed for torsion load.
Torsion is the twisting motion with which a torque is tangential to the cable axis.
Bending is the twisting motion with which a torque is radial to the cable axis.
Is the jacket material resistant against certain chemical substances?
Please consult the "Chemical Stability of PVC and PUR Cable Jackets" overview in the download section.